Lightning Protection CAT6 Single Channel Ethernet Indoor Surge Protector
|1-49 50-99 100-999 1,000-9,999 10,000+|
|FOB Unit Price:||US $25 US $18 US $16 US $12 US $6|
|Purchase Qty. (Pieces)||FOB Unit Price|
|Production Capacity:||500, 000PCS/Year|
|Payment Terms:||L/C, T/T, Western Union, Paypal|
- Model NO.: SNH-RJ45
- Type: Wireless
- Information content: Data
- Condition: New
- Max Discharge Current(Ka): 5ka
- Dimension (mm): 100(L) ×87(W) ×28(H)mm
- Weight Per Unit: 120g
- Protection Line: 1-8
- Interface Form: Interface Form
- Transport Package: Carton
- Origin: China
- Usage: Computer, Workstation, Server, Laptop
- Support Network: Ethernet
- Certification: CE, ISO, RoHS, FCC, National Type Test
- Max Continuous Operating Voltage: 6V
- Transmission Rate (Mbps): 100Mbps
- IP Code: IP20
- Insertion Loss Ae: 0.5dB
- Response Time Ta: 1ns
- Trademark: OPPLEI
- Specification: CE, FCC, ISO9001, RoHS, China National Type Test
- HS Code: 8535300000
|Thank you for choosing Cat6 Surge Protector SNH-RJ45. The model is designed to protect high-speed communication network from lightning over-voltage, transient over-voltage and static discharge. The protector implements multi-level protection circuit with advanced manufacturing process, and has excellent performance on discharge current, limiting voltage, response time, stability and over-all reliability.|
Multi. Protection circuits, Gas-Tube+ TVS technology
Dual protection in Common module and different module
TVS array technology, low capacitance
|Max. continuous operating voltage Uc||6V|
|Nominal discharge current(8/20µs)In||2.5kA|
|Max. discharge current (8/20µs)Imax||5kA|
|Limiting voltage (10/700µs) Up|
|Adapt transmission rate||1000Mbps|
|Insertion loss Ae||0.5dB|
|Response time Ta||1ns|
|Dimension||100(L) ×87(W) ×28(H)mm|
|Weight per unit||120g|
|Working conditions||Temperature: -40 to 80ºC, Relative humidity: ≤95%|
|Standards Compliance||CE, FCC, RoHS,ISO9001|
INSTALLATION AND MAINTENANCE
a) The SPD should be connected in series between the protected device and the signal/power transmission channel.
b) The input terminal (IN) of the SPD should connect to the signal/power transmission channel, and the output terminal (OUT) of the SPD should connect to the protected device.
c) Connect earthing wire of the SPD to earthing bus-bar of the lightning protection system of the room or building.
No special duty needs to be carried out for maintenance. When problem arises and the SPD is suspected, check the system with SPD taken out of circuit. Should system recover, the SPD shall be regarded as a damaged unit and must be replaced immediately.
Q: Can I get some samples?
A: Yes, Sample orders welcomed.
Q: Can I use my own Logo or design on goods?
A: Yes, Customized logo and design on mass production are available.
Q:What is the delivery time?
A: 3 days for samples, 7-10 working days for mass production after payment.
Q: What is the payment term?
A: T/T, L/C at sight, West union , Paypal, etc
Q: Can I trust you?
A: Absolutely YES, We are "Made In China" verified supplier for many years.
Q: May I visit your factory?
A:Sure, welcome any time. We can also pick you up at airport or station.